Contact the seller — opens in a new window or tab and request a shipping method to your location. Any visible signs of damage to the shipping packages should be reported to General Electric Canada immediately. See other items More If necessary, use a reducing bushing. Alla procedurer i manualen m?
|Published (Last):||5 June 2016|
|PDF File Size:||9.84 Mb|
|ePub File Size:||1.13 Mb|
|Price:||Free* [*Free Regsitration Required]|
Kagazuru These caps protect the adaptor threads see Figure on page and the sensor membrane see Figure on page from debris and sharp objects. Furthermore, to ensure optimum performance of the HTi, the diameter should not exceed 76 mm 3 in.
Seller information garlandequipment Back to home page. This location presents the HTi with the best combination of oil flow, temperature and ease of access. Calculate Varies based on location and shipping method.
Add to watch list Remove from watch list. See all condition definitions — opens in a new window or tab. If these four recommended locations cannot be used, contact the General Electric Canada Customer Service see the coordinates at the bottom of page ii to help you determine an acceptable alternative location.
If Products covered by this manual do not meet the above warranties during the applicable Warranty Period, the Buyer shall promptly notify General Electric Canada in writing but not later than 30 days and make the Products available promptly for correction. Suwanee, Georgia, United States. For complete explanations on the installation process, refer to the Hydran i System Instruction Manual. To help the reader, a Table of Contents and a List of Figures are present at the beginning of the manual.
Use a bucket to collect the oil. Interest will gydran charged to your account from the purchase date if the balance is not hydtan in full within 6 months. Wait a few minutes and touch the back of the heating plate. Local logging of data and significant events for up to a year. The HTi requires set-up alarms, temperature, data logging and commissioning for normal use.
Please refer to the Hydran i System Instruction Manual. If necessary, use a reducing bushing. Figure — Do Not Touch the Membrane. Shipping cost cannot be calculated. Please enter 5 or 9 numbers for the ZIP Code. Be careful when installing and inserting each wire. Learn More — opens in a new window or tab International shipping and import charges paid to Pitney Bowes Inc.
Please enter a number less than or equal to 1. Resume making your offerif the page does not update immediately. Easy to install on a single valve. Please keep all documentation model number, manuals, etc. Pipe wrench to tighten the brass adaptor onto the valve? Strip each wire to a maximum of 8 mm before installing it. Dispose of the collected oil according to company standards. Much better than relying on manual oil sampling.
Please enter a number less than or equal to 8. Used during the cleaning of transformers, they may cause serious damage. The body of the valve must be grounded. When there are tj more air bubbles present in the oil, shut the bleed screw tightly. An item that has been professionally restored to working order by a manufacturer or manufacturer-approved vendor.
Proceed carefully to avoid introducing air into the transformer. Inspect the adaptor and sensor for oil leaks. Do not install the HTi on the tii side of the radiator pump see Figure on page When the HTi is installed horizontally, the terminals must be facing up and located under the sensor. Fasten the module with the two screws see Figure on page New without original box.
Install the HTi horizontally; not at an angle, vertically or horizontally using an elbow see Figure on page Seller information viper Related Posts
Hydran 201Ti Transformer Monitoring System
It provides continuous monitoring of gas and moisture levels to alert users of developing faults and minimize the risk of unplanned outages. Benefits Small form factor, no moving parts, low maintenance Easy to install on a single valve Condition monitoring for a wide range of transformers with mineral insulating oils or ester based fluids natural and synthetic Real-time composite gas or hydrogen only and moisture in-oil measurement system Automatically alert users of developing fault conditions Supports a wide range of communication methods and protocols Expandable with transformer models capabilities using additional sensors Integrated display and keypad for simplified local user interaction and data visualization 7 year product warranty An example of using external input sensors with Hydran M2-X for transformer models calculations Applications All-in-one solution for important medium size transformers Focuses and prioritizes asset replacement strategy Reduces the risk of process interruption due to power failure Minimizes costly production downtime.
GE hydran m2 Installation Manual
The following details important considerations for the installation of the HTi: 1. Mount the HTi on a full-bore gate valve preferred or a ball valve where there is a good forced or convective oil flow. Install the HTi on a valve with a diameter of 38 mm 1. The recommended location to mount the HTi is on a straight section of the cooler return pipe, and on the discharge side of the pump if present. This location presents the sensor with the best combination of oil flow, operating temperature range and ease of access. Recommended Locations 2.
Vur Run the supervisory link cable into the conduit up to the HCi Controller the electrical connections drawings can be found in Appendix A. Full system self test and self-diagnostics. See all viper has no other items for sale. Select a valid country. If necessary, use a reducing bushing. Please read Chapters 2 and 3 before proceeding.
Ge hydran m2 Manuals